ANSI TIA EIA 606A PDF
ANSI/TIA/EIAA Approved: May 16, TIA/EIAA. Administration Standard for. Commercial Telecommunications. Infrastructure. TIA/ EIAA. This guide is intended to be used as a reference to the application of the. ANSI/ TIA/EIA A Standard. It in no way reflects all the necessary infor-. ANSI/TIA/EIA Administration Standard for the. Telecommunications Infrastructure of. Commercial Buildings. Distributed by NDS INFORMATION- TELECOM.
|Published (Last):||18 February 2007|
|PDF File Size:||15.22 Mb|
|ePub File Size:||5.18 Mb|
|Price:||Free* [*Free Regsitration Required]|
While recommended, color coding is not required, and compliant coding may be accomplished using color labels or color bands. The following is the color coding scheme recommended in B:.
The following is a simple example of a cable identifier. It identifies the termination point for both ends of the 066a, with the near end shown first.
This is port A04 — As before, the first element identifies the cabinet location, but this time for the far end of the cable.
This particular cable would have a corresponding label on the other end the data center end, in this case which would read:. The labeling ansk that underlie B include the following: Labeling must be logical and consistent, across all locations, matching the project drawings.
UTP Link Performance Marking and Identification – Siemon
The labeling znsi must identify the associated physical locations building, room, cabinet, rack, port, etc. Labeling must be easily read, durable, and capable of surviving for the life of the component that was labeled.
The labeling system, and the identifiers used, must be ansj upon by all stakeholders. Labeling should be pervasive; cables and connecting hardware should be labeled, but so should conduits and firestops, grounding and bonding locations, racks, cabinets, ports, and telecommunications spaces.
structured cabling test Chapters 9,10,11,12,13 Flashcards Preview
These principles are then translated into specific requirements. Requirements For Labels All labels must use a permanent identifier that can be easily traced — that is, a useful numbering scheme. This scheme must be logical in its organization, using alphanumeric characters for ease of reference.
Each cable and each pathway must be labeled on each end, and each label should identify the termination points of both ends of the cable. All labels must meet requirements for legibility, defacement, and adhesion, specified in UL Labels for station connections may appear on the face plate. All jack, connector, and block hardware may be labeled on either the outlet or panel. All labels must match up with the permanent record.
Wire Color Coding While recommended, color coding is not required, and compliant coding may ahsi accomplished using color labels or color bands.
ANSI TIA B Cable Labeling Standards | Graphic Products
The following is the color coding scheme recommended in B: PVBX, LANs, and individual computers Yellow — Auxiliary circuits, such as alarms and security systems Red — Key telephone systems termination Record Keeping Requirements Drawings and documents must be secured and backed up by the building administration.
Any moves, adds, and changes MACs must be documented with a change order.
MACs must be recorded and updated in the permanent records. Permanent records must cross-reference all identifier information. This particular cable would have a corresponding label on the other end the data center end, in this case which would read: